Hi there, in my kitchen (well dining room but its open plan, may have part p implications) where i want to put my tumble dryer there is a blanking/access plate (single) which contains a 2.5 te cable connected to the amoured cable via a block which feeds the garage breaker radial circuit and lights. This 2.5 te cable is fed from the cu on a 16 breaker and the cu is a dual rcd unit (new build house 2015). my question is can i change the blanking plate for a single socket and feed the tumble dryer from this socket? i know dryers can be hungry so whats the implications of this? and if i can do it, can i do it myself? its just connecting a faceplate but unsure if this falls under part p or not?